If field verification cannot be conducted, the material may not be
approved or accepted by the Lafayette Fire Prevention Bureau and the
material will have to be removed.
Due to the availability of a
wide variety of foam products, we strongly suggest speaking with an
Inspector prior to installing any product to avoid the possibility of
having to remove the product and reinstalling an approved material.
When using Dow Foam Sealant for Fire Blocking
installation of the foam sealant must comply with the ESR-1961 Report
and the manufacturer's published installation instructions.
- The Conditions of Use outlined in the ESR-1961 Report shall be followed.
- All used containers must be kept onsite for Inspector's verification.
Can Great Stuff Spray Foam Insulation Be Used as a Fire-Stop System?
No, a fire-stop system includes a product which has been tested under
certain conditions, and performed to maintain the rating of the assembly
at the point of penetration or joint. The Dow polyurethane foam is not
included in the ICC-ES Evaluation Report as a suitable material for
membrane or through penetration of a fire-resistance-rated assembly.